Tripp Lite 3 phase Metered PDU / Power Distribution Units offer real-time local reporting of output current output kW and input voltage via built-in multifunction digital display. Enables visual monitoring of PDU current levels to preserve proper loading balance and prevent circuit overloads as additional equipment is added. Offers reliable rackmount multi-outlet power distribution from any protected UPS generator or mains input power source. High quality design includes rugged all-metal housing and secure rackmount installation with included mounting accessories.&lt;br /&gt;&lt;br /&gt;- Metered 22.2kW 3 Phase 380/400V input 220/230V output PDU&lt;br /&gt;- Visual meter reports output amps per bank total kW and input voltage&lt;br /&gt;- IEC309 32A Red (3P+N+E) 3 phase 380/400V input 6 ft. / 1.8m line cord&lt;br /&gt;- 42 220/230V outlets (36 C13 6 C19) with included plug-lock cord retention sleeves &lt;br /&gt;- 0U Vertical Rackmount with Toolless button-mount installation&lt;br /&gt;&lt;br /&gt;- 22.2kW 3 phase 380/400V input 220/230V output Metered Power Distribution Unit / PDU&lt;br /&gt;- Visual display with scroll function enables selection of breakered load banks 1-6 for output current reporting in amps total kW output and PDU input voltage&lt;br /&gt;- Attached IEC309 32A Red (3P+N+E) 3 phase 380/400V input 6-ft. / 1.8m line cord&lt;br /&gt;- 0U 70 in. / 178cm vertical form factor supports installation in 2 or 4 post equipment racks&lt;br /&gt;- 42 total 220/230V outlets (36 C13 6 C19) arranged in 6 separately breakered single phase output load banks&lt;br /&gt;- Included cord retention sleeves keep vital network equipment plugged in and continuously powered&lt;br /&gt;- Toolless mounting supported in button-mount compatible racks plus nut-and-bolt mounting brackets for other mounting applications (set of 2 9mm buttons pre-installed 2 9mm and 4 6mm spare buttons included)